Keep Your Home Comfortable With Quality HVAC Services In North Branford CT
X-Treme Temp Heating & Cooling is your go-to HVAC service provider in North Branford, CT! We’re the experts in home comfort year-round, from AC and heating repair to ductwork and water heaters. We’ve got you covered from installation to maintenance so you can have peace of mind about your heating and air conditioning.
Read the reviews below from North Branford, CT residents to see what your neighbors say about our expertise and customer service. We can’t wait to work with you!
for North Branford, CT
Our Reviews by City
Performed a heating pm on an oil furnace and hot water heater. Brushed and vacuumed. Replaced oil filter, nozzles, and strainers. Checked electrical connections and safeties. Performed a combustion test. Systems are operating properly. Bock 51E
Arrived on site and turned water heater off. Removed old porcelains and replaced with new porcelains. Started and tested unit. Unit is working properly.
Brushed and vacuumed flu pipes and heat exchangers Replaced oil filter, nozzles, and strainers Checked all electrical connections and safeties Preformed combustion and smoke tests When cleaning up after the service we found a small pinhole leak on the bottom of the oil canister. Replaced the bottom half of the oil canister with a new one. Also found that the porcelain on the water heater jtube had cracked. Took pictures and measurements for replacement. Furnace-12.0%o2 42ppm co 0 smoke Water heater-8.2%o2 29ppm co 0 smoke While testing the furnace there was a spike in o2 when the blower turned on indicating a crack in the heat exchanger. The o2 went from 5.6%o2 to 12.0%. Recommended replacing furnace soon before the crack causes issues with the heat. Quoted price for porcelain repair is 110 plus tax
Upon arrival found large section of oil line that was very porous and leaking. Pushed back all oil from oil line into oil tank. Removed old oil line, and installed new oil line in its place. Bleed the air from oil line and fired the unit. Checked for leaks around new connections, no leaks found. Recommend having a maintenance performed on the furnace. Signed up for bronze maintenance agreement.