Get Reliable HVAC Service today in Waterbury CT!
The heating and cooling seasons are pretty equal in Waterbury, CT, which means that having a well operating heating and air conditioning system is important. To ensure that your HVAC system is operating properly, you should have it serviced twice a year and replaced once it reaches the end of its service life. Once your heating and air conditioning system reaches the end of its service life, it will not cool and heat your home effectively or efficiently. Luckily, at X-Treme Temp we can help with any HVAC need you have!
for Waterbury, CT
Our Reviews by City
Upon arrival unit was off. Turned on and condenser turned on but air handler did not. Upon inspection found that the capacitor for the indoor blower was open internally and was not supplying the blower with power to start. After getting customer authorization we replaced the capacitor for the indoor blower and tightened the terminals on the thermostat housing. Started unit and checked refrigerant levels. Unit is operating properly and had a 19° temp difference.
Brushed and vacuumed flu pipe and heat exchanger Replaced oil filter, nozzle, and strainer Checked all electrical connections and safeties Preformed combustion and smoke tests 6.9%o2 29ppm co 0 smoke Visually inspected indoor evap coil and blower compartment Checked all electrical connections and safeties Checked volts and amps Visually inspected air filter. Replaced with customer supplied Rinsed condenser coil Blew out drain line and poured water to ensure properly draining Tested condensate pump Checked refrigerant levels Checked capacitor Took temps Replaced capacitor after getting customer approval due to it being well outside of factory specs. Duct diagnostics 203 734 1532