Get Reliable HVAC Service today in Middlebury CT!
The heating and cooling seasons are pretty equal in Middlebury, CT, which means that having a well operating heating and air conditioning system is important. To ensure that your HVAC system is operating properly, you should have it serviced twice a year and replaced once it reaches the end of its service life. Once your heating and air conditioning system reaches the end of its service life, it will not cool and heat your home effectively or efficiently. Luckily, at X-Treme Temp we can help with any HVAC need you have!
for Middlebury, CT
Our Reviews by City
The burner was off on reset. The customer just had 290 gal delivered. The tank is a 330. It was out of oil prior to delivery. Bled the oil line until there was clean oil coming out of the bleeder port. Checked the system. The burner is operating properly. The water on the floor is from the boiler being cold and the gaskets shrunk. After the boiler heated up the water stopped dripping from the domestic coil gasket. The system is operating properly.
Brushed and vacuumed flue pipe and heat exchanger Replaced oil filter, nozzle and strainer Checked all electrical connections and safeties Performed combustion and smoke tests 6.1%o2 45ppm co 0 smoke
Oil pm Brushed out unit and vacuumed soot Replaced filter nozzle strainer Tested unit the unit was running at 3.3%o2 and 22 ppm of co. Customer is going to need a new domestic water coil. Due to excessive corrosion we cannot just replace the gasket. Also the boiler is going to need a mixing valve. He is complaining on how the water is scorching hot than cot then scorching hot again. Mixing valve quote $814.17 plus tax On the Ac pm check list A was designated for the attic unit and B was the basement unit Everything was working properly for the ac system