Keep Your Home Comfortable With Quality HVAC Services In Southington CT
X-Treme Temp Heating & Cooling is your go-to HVAC service provider in Southington, CT! We’re the experts in home comfort year-round, from AC and heating repair to ductwork and water heaters. We’ve got you covered from installation to maintenance so you can have peace of mind about your heating and air conditioning.
Read the reviews below from Southington, CT residents to see what your neighbors say about our expertise and customer service. We can’t wait to work with you!
for Southington, CT
Our Reviews by City
Great service. Very clear explaining the problem and what needs to be done.
MAS - Southington, CT 06479
Found that the customer changed the thermostat and didn’t push the wires into the wall. This made the thermostat not click in to the base like it should which wasn’t sending a signal to the furnace. Redid the wires and tested. The thermostat sits flush and turns the furnace on and off as needed.
Brushed and vacuumed flu pipe and heat exchanger Replaced oil filter, nozzle, and strainer Checked all electrical connections and safeties Preformed combustion and smoke tests 7.4%o2 44ppm co 0 smoke Had to replace 1 clean out cover due to the bolt snapping while removing it. While preforming maintenance found that the thermal limit disc was getting stuck around 100 degrees and not rotating to turn the fan on. After manually rotating the limit disc, it was operating properly for the remainder of the maintenance. The limit disc might fail in the future causing the blower to not turn on. Took pictures of the model and the part so if the limit does fail we will be able to order a replacement.
Furnace Repair and Heating Service - Removed and replaced the furnace control board. Started and tested the operation several times. The system is operating properly.
Upon arrival found that the condensate line had broken off inside the wall and was now between the inside and outside walls. Cut vinyl tubing above ceiling grid and joined it with a longer section to run it over to the sink so the ac could be run temporarily. Need to have plumber come and cut a tap into a drain stack so the tubing can be rerouted to avoid any issues with draining come winter time.
Preformed ac maintenance check list. Everything was working properly with no concerns