Keep Your Home Comfortable With Quality HVAC Services In Cromwell CT
X-Treme Temp Heating & Cooling is your go-to HVAC service provider in Cromwell, CT! We’re the experts in home comfort year-round, from AC and heating repair to ductwork and water heaters. We’ve got you covered from installation to maintenance so you can have peace of mind about your heating and air conditioning.
Read the reviews below from Cromwell, CT residents to see what your neighbors say about our expertise and customer service. We can’t wait to work with you!
for Cromwell, CT
Our Reviews by City
Visually inspected indoor evap coil and blower compartment Checked all electrical connections and safeties Checked volts and amps Visually inspected air filter. Rinsed condenser coil Blew out drain line and poured water to ensure properly draining Tested condensate pump Checked refrigerant levels Checked capacitor Took temps After getting customer authorization we replaced the capacitor due to it being under factory specifications
Upon arrival found the flue pipe to be paper thin and falling apart. Repair was quoted out at $285. The homeowner approved of the repair for $285. Removed section of old flue and installed new flue pipe in its place. After repairing flu pipe, an oil maintenance was performed. Brushed and vacuumed soot and debris from the heat exchanger. Checked electrical connections and safeties. Performed a combustion test on unit, unit is running at 5.4% O2, 20ppm CO, with zero smoke. 30 dollar discount was added for heating maintenance.
Removed old timer control board and replaced with new one. Started and tested unit. Unit is running at 8.6%o2 20ppm co. Unit is working properly. Need to return to replace mixing valve gaskets. Took pictures and uploaded them to companycam.
Upon arrival the compressor and the suction line was iced up. Because it was so hot out the ice melted quickly. We found the air filter was extremely dirty. Replaced the air filter. It was a 25x16x1. The humidifier that was on the back of the furnace has melted and left a gaping hole in the ductwork. It was disabled and non functional so We removed the humidifier and patched the ductwork. I had to add 2lbs of r22 refrigerant. There was a 18*f delta t. The unit is working properly. The unit is from 2001. Also noticed that the flue pipe for the furnace was paper thin and very brittle. Will need to quote out a price to replace it before heating season.